1. PUMPS FITTED WITH OIL LUBRICATED BEARINGS
1.1 Oil Specification
|OIL LUBE||OIL SPECIFICATION|
|QTY(ml)||Preferred oJSs are those that have non foaming properties.
Typicatfy, twbsne of hyctfauiic osts wotitct be stiitable.
Viscosity of SAE20 to SAE30 (ISO VG 46 to 100).
Automotive os!s wotitct be stiitabie in light dufy cycles.
|1||450||Light Duty – Less than 8 hours/day or intermittent
Tellus 46 or 68, or Turbo T46 or T68.
|2||800||Heavy Duty – Greater than 8 hours/day or continuous
Tellus 68, Turbo T68 or Madrella AS68.
|3||1200||Low Temperature – Less than 10 to -30 degrees Celsius
Refrigerator Oil 68K.
Bearing housing temperature should not exceed 80 degrees Celsius in normal circumstances.
higher temperatures are noted, use an oil of lower viscosity.
When pumping product of elevated temperature, it may be advisable to have oil cooling fitted to
maintain an acceptable bearing housing temperature.
Consult dealer for maximum operating speeds
1.2 Change interval
|TYPE OF SERVICE||HOURS OF SERVICE|
|LIGHT DUTY||Change oil after 2000 hours service|
|HIGH TEMPERATURE||Change oil after 1000 hours service|
|HEAVY DUTY||Change oil after 1000 hours service|
Post time: Jun-19-2019