How To Install The Submersible Sewage Pump?
Submersible sewage pump is the abbreviation of submersible sewage pump. On the basis of submersible pump, the channel adopts anti-clogging design, which is used for primary lifting, intermediate lifting and sludge return. Mainly used in municipal engineering, building construction, industrial sewage and sewage treatment occasions, to discharge sewage, wastewater and rainwater containing solids and long fibers.
Two Commonly Used Installation Methods:
The submersible sewage pump has simple installation conditions and a large flow coverage. It is one of the most commonly used lifting equipment in water treatment projects, especially in small and medium-sized projects. There are mainly two common installation methods for submersible sewage pumps: coupled installation and mobile installation.
Coupling Installation is to connect the pump to the pipeline through a coupler, and it is convenient to disconnect the pump from the outlet pipe. The pump can be lifted by the lifting device during maintenance. Coupling installation is suitable for submersible sewage pumps of various specifications and is the most commonly used installation method for submersible sewage pumps. The coupler is supplied as a complete set by the equipment manufacturer.
Mobile Installation means that the pump outlet pipeline is directly connected to the water surface through a hose, and the submersible sewage pump is self-reset at the bottom of the pool or hung on the lifting device through iron chains. The mobile installation does not require a coupler and the bottom of the pool to be fixed, so it is easy to move, and the pipeline can be lifted together during maintenance. At the same time, due to the installation method, it is difficult to bear a large torque, which is only suitable for small submersible pumps.
Post time: Jul-31-2020